Learn more about blade orientation and how it can affect a control damper's performance.
Parallel or opposed? When choosing a control damper, this question may seem like the least of your worries. The orientation of your blades has minimal effect on the damper in the open position, but the way they come together is important when they close. This is where the control damper’s blade orientation becomes important.
Parallel and Opposed
Blade orientation refers to the way blades are installed in a control damper or an adjustable louver. The blade orientation can be either parallel or opposed.
Parallel orientation means that every blade moves the same way when opening and closing. Every blade will be at the same angle in the fully open position. During closure, the front edge of each blade will come together with the back edge of the blade below it. These edges overlap to close off the damper. Dampers are often depicted with parallel blades, because the blade movement is uniform across the damper's face.
In opposed orientation, each blade will have a different blade angle than its neighbors. Imagine assigning a number to each blade. Odd blades will all have the same blade angle and even blades will also have the same angle.
While opening and closing, the odd blades will move in the opposite direction of the even blades. Like the parallel blades, the edges of the opposed blades will overlap when the damper closes.
The Difference Between Parallel and Opposed
While the results may look the same, these two blade orientations have trade offs that make them better suited for certain applications. When opening and closing, parallel blades minimize pressure drop through the damper’s blades. This makes parallel blade orientation the best orientation for maintaining air flow.
In opposed orientation, the movement of the opposing blades can increase pressure drop while opening and closing. This can put undue strain on your HVAC system every time the damper operates. Parallel blade orientation is best for dampers that regulate airflow through duct work.
Why choose opposed blade orientation? While they may affect airflow, opposed blades do serve an important role in your HVAC system. The opposed blade action can provide more torque to the blades while in the closed position. This action creates a tighter seal between each blade and minimizes air leakage in the process. Opposed blade orientation is best for directing airflow to different parts of the building.
Choosing the right blade orientation will ensure your dampers are designed for peak HVAC efficiency, saving you money over the lifetime of the system.
MCDLG & Continuing Education
MCDLG offers free self-paced courses online through AEC Daily. Each course is self-paced and provides continuing education credits for a variety of institutions, including ASHRAE's PDUs and learning units from AIA. Learn and earn credit at your own pace. Visit the MCDLG Online Campus portal today!